Quotation for maintenance of diesel generator sets
Check the diesel engine oil and coolant levels, fill up when inadequate, rent the generator and check the cause of insufficient cooling water; check the tightness of the cooling fan and charger belts of the diesel engine.
Check whether all the hoses and joints of the generator set are loose or frayed. If there is any, tighten or change them; Check if the battery pile head can be corroded, if it is clean, check the battery fluid level, and add battery fluid if necessary.
Check whether there is abnormal noise when the generator set is started. Change the oil grid. Diesel grid atmosphere. Oil-water separator filter. Check the components and the price of the generator set circuit that can be changed normally. Caltex oil drum. Yuan / barrel. One set. One set of yuan atmosphere. One set of labor costs for recuperation. The total amount of remarks:
- Blue smoke, fire reason: It means that the engine is burning oil. There are three types of reasons: first, the piston ring goes opposite, and the oil comes in the cylinder; the second is the oil level of the oil pan of the atmosphere filter, which leads the ring. The height of the groove; Third, the gap between the duct and the valve stem is too poor. Expulsion idea: Adjust the piston ring so that the opening teeth of the ring are staggered 120 degrees or 180 degrees, and the opening teeth of the ring should avoid the piston pin hole and the side pressure is poor. Adjust the height of the oil level of the oil filter of the atmosphere filter below the height of the annular groove; if the clearance between the duct and the valve stem is too poor, replace the component and reduce the clearance. The normal mutual assistance clearance between the two is 0.0
- In the power generation industry in China, we have been working hard, pursuing the concept of quality and service, and for the sake of customers, the full power generator chooses China and your generator is a professional housekeeper. At present, the diesel generator set maintenance market refers to damage inspection and routine maintenance. Two aspects: after maintenance refers to the failure of the diesel generator, there are problems with various accessories, such as replacing the generator or
- The diesel engine is working normally, but the generator fails to generate electricity or the voltage is very low. This may be due to the components associated with the generator, such as: the exciter is damaged, and the excitation voltage cannot be supplied. The excitation current is taken in. The rotor's dead center residual magnetism is weakened or declining. It will make the generator unable to generate electricity or the transmission voltage is extremely low. The right to respond is usually: use an appropriate DC voltage and directly connect to the excitation winding according to the polarity Magnetization. Carefully inspect the exciter and the cyclotron rectifier, find abnormal components or windings, and replace them for restoration. The generator's transmission voltage is unstable, and
- Before starting, you should check whether the fuel volume of the fuel tank is rich, and there is no oil leakage in each oil pipe and the discussion area; whether the cooling system water is rich, clean and leak-free, and whether the fan belt is tight or not. The internal combustion engine and generator drive parts should be connected and trusted. The wires of the input line are well-insulated, complete and effective in all aspects. After starting, it should run at low speed for 3 to 5 minutes. After the temperature and oil pressure wheel are normal, the initial work can be done. The generator should be no different in the speed increase. Ring, the slip ring and commutator are well brushed, no jumping and sparking phenomenon. After the operation is stable and the frequency and voltage reach the rated value, power can be supplied to the outside.
- What are the problems and common faults of the generator fault light
- Relevant knowledge and cleaning methods of diesel generators
- Reasons for the failure of diesel generators and their applications
- Common problems and errors of diesel generators
- Introduction of generator inspection content and its structure
- Problems and maintenance of generators in work
- Drainage regulations for diesel generators and faults
- Explain the diesel generator fault treatment method and its
- Precautions and machine when using diesel generators
- What are the specific operating methods for diesel generators?