Principle of Diesel Generator Power Distribution System
The generator recovers the diesel generator power distribution system. The generator rents out the diesel generator power distribution output. It is output through the plastic case circuit breaker on the side of the unit that matches the capacity of the unit. The circuit breaker is in the open cover on the side of the unit. It can be operated directly by the handle for closing and opening.
The purpose of the air switch is to protect the alternator of the unit from being damaged by overloading or other abnormal impacts. The air circuit breaker has a high breaking capacity and automatic tripping capacity when faults occur. When the user of Zhongshan Generator leases power, he can directly draw the cable from the lower end of the air circuit breaker to his own load.
There is no plastic circuit breaker in the open circuit hood of the high-power generating unit or parallel generating unit to generate the power output screen or parallel screen. The power generation output control protection is replaced by the main circuit breaker in the above screen.
When installing the power distribution output of the unit, the user configures the cable that meets the safe full ampacity to the power output screen or parallel screen, and ensures that the phase sequence of the power output is correct.
- The diesel engine is working normally, but the generator fails to generate electricity or the voltage is very low. This may be due to the components associated with the generator, such as: the exciter is damaged, and the excitation voltage cannot be supplied. The excitation current is taken in. The rotor's dead center residual magnetism is weakened or declining. It will make the generator unable to generate electricity or the transmission voltage is extremely low. The right to respond is usually: use an appropriate DC voltage and directly connect to the excitation winding according to the polarity Magnetization. Carefully inspect the exciter and the cyclotron rectifier, find abnormal components or windings, and replace them for restoration. The generator's transmission voltage is unstable, and
- In the power generation industry in China, we have been working hard, pursuing the concept of quality and service, and for the sake of customers, the full power generator chooses China and your generator is a professional housekeeper. At present, the diesel generator set maintenance market refers to damage inspection and routine maintenance. Two aspects: after maintenance refers to the failure of the diesel generator, there are problems with various accessories, such as replacing the generator or
- Before starting, you should check whether the fuel volume of the fuel tank is rich, and there is no oil leakage in each oil pipe and the discussion area; whether the cooling system water is rich, clean and leak-free, and whether the fan belt is tight or not. The internal combustion engine and generator drive parts should be connected and trusted. The wires of the input line are well-insulated, complete and effective in all aspects. After starting, it should run at low speed for 3 to 5 minutes. After the temperature and oil pressure wheel are normal, the initial work can be done. The generator should be no different in the speed increase. Ring, the slip ring and commutator are well brushed, no jumping and sparking phenomenon. After the operation is stable and the frequency and voltage reach the rated value, power can be supplied to the outside.
- Blue smoke, fire reason: It means that the engine is burning oil. There are three types of reasons: first, the piston ring goes opposite, and the oil comes in the cylinder; the second is the oil level of the oil pan of the atmosphere filter, which leads the ring. The height of the groove; Third, the gap between the duct and the valve stem is too poor. Expulsion idea: Adjust the piston ring so that the opening teeth of the ring are staggered 120 degrees or 180 degrees, and the opening teeth of the ring should avoid the piston pin hole and the side pressure is poor. Adjust the height of the oil level of the oil filter of the atmosphere filter below the height of the annular groove; if the clearance between the duct and the valve stem is too poor, replace the component and reduce the clearance. The normal mutual assistance clearance between the two is 0.0
- What are the problems and common faults of the generator fault light
- Relevant knowledge and cleaning methods of diesel generators
- Reasons for the failure of diesel generators and their applications
- Common problems and errors of diesel generators
- Introduction of generator inspection content and its structure
- Problems and maintenance of generators in work
- Drainage regulations for diesel generators and faults
- Explain the diesel generator fault treatment method and its
- Precautions and machine when using diesel generators
- What are the specific operating methods for diesel generators?